Scott T Transformers are not suitable for the following applications:
Scott T offers dual single phase outputs (50% each). If only one single phase output (100% each) is required, then Scott T will not work. Refer to the link to http://www.lcmagnetics.com/other-projects/three-phase-to-single-phase-transformer-pn-6411l/
On Scott T transformers the Main and Teaser outputs cannot be connected in series or parallel.
The schematic of a Scott T Transformer is shown below. The Scott T works in the reverse configuration as well. For example if input is (X1, X2) and (Y1, Y2), then output will be (H1, H2, H3).
A Scott T Transformer is built with two single phase transformers of equal power rating. The MAIN and TEASER sections are enclosed in a floor mount enclosure. The MAIN is installed in the bottom section and the TEASER is installed on the top section. A jumper is used to connect the MAIN and the TEASER.
The MAIN and TEASER can be placed side by side in separate enclosures as well and connected with a jumper.
L/C Magnetics can build Scott T Transformers with power rating from 1 KVA to 500 KVA. All units are custom designed and built to customer specifications.
Content is presented in two formats, PHOTO FORMAT and TABLE FORMAT. The PHOTO FORMAT is shown first. The TABLE FORMAT is shown after the PHOTO FORMAT.
PHOTO FORMAT – SCOTT T TRANSFORMERS
The table below can be viewed in ascending or descending order for all categories such as P/N, Input (VAC), Output (VAC), Output (Amps), KVA ot Type. Click the Part Number to view more details and additional tap information. Only one tap detail is shown in the table.
TABLE FORMAT – SCOTT T TRANSFORMERS
|P/N||Input (VAC)||Output (VAC)||Output (Amps)||KVA||Type|